HORIZONTAL PACKAGE AIR CONDITIONNERS 50HB/HF
Installation - Switchable position of dischage and return of the indoor / outdoor circuit. This allows to leave the unit as most vonvenient in each installation. Please see the possible assembly types. - Shock absorbers made of rubber Outdoor ambient - INERA® coils (outdoor and indoor) with copper pipes and ﬁns of an aluminium alloy, of high performance and great resistance to the corrosion - Coils (outdoor and indoor) with copper pipes and aluminium ﬁns with polyurethane coating - Condensation pressure control with damper Comfort / heating - Electrical heaters support. With this option, the air ﬂow controller is included. Indoor air quality - Indoor circuit: gravimetric ﬁlter G4 - Indoor circuit: gravimetric ﬁlter G4 + creased opacimetric ﬁlter F7 Acoustics - Compressor acoustic isolation Safety - Differential pressostat for dirty ﬁlters - Differential pressostat for control of air ﬂow Electric panel - Power supply with neutral Control / Comunication Optional for the CARRIERrtc basic electronic control: • pGD1 terminal to maintenance of the unit • Temperature probe of the return or ambient air connected to the control board that replaces the ambient probe of the TCO thermostat. This probe performs necessary for the anti-ﬁre safety. Connection to a centralised technical management system by using a especiﬁc BMS card for some of the communication protocols: • RS485 serial cards for network communication with protocols: Carel, Modbus, LonWorks®, BACnetTM MSTP, Konnex. • Ethernet pCO Web card for network communication with protocols: Modbus TCP/IP, BACnetTM Ethernet, TCP/IP, SNMP V1-2-3, FTP and HTTP. Solutions of supervision: exists 3 different solutions according to the dimensions of the installation: pCO Web (only one unit), PlantWatchPRO3 (up to 30 units), PlantVisorPRO2 (up to 300 units).
16 available combinations for the air circulation
Two possible directions for the air supply of the indoor circuit
Switchable panels for the air return of the outdoor circuit
Switchable panels for the air return of the indoor circuit
Two possible directions for the air supply of the outdoor circuit