DUCTABLE AIR-TO-WATER HEAT PUMPS 30RQSY 039-160
Legend: All dimensions are given in mm
Control box Water inlet Water outlet 1 2 Required clearances for air entry Recommended space for maintenance Air outlet, do not obstruct Power supply inlet * Overall dimensions
Notes: A Non-certified drawings. Refer to the certified dimensional drawings supplied with the unit or available on request, when designing an installation. For the location of fixing points, weight distribution and coordinates of the centre of gravity refer to the certified dimensional drawings. B Provide a gutter around the unit to collect the condensate water or install the accessory condensate collection pan (30RQSY 039-078). C The unit must be installed level (less than 2 mm per metre deviation in both axes). D Units 30RQSY 039-078 are equipped with a sleeve on the air heat exchanger side to allow connection of a suction air frame.