61AF 022-035 units with and without hydronic module
Legend All dimensions are in mm Required clearances for air flow Recommended space for maintenance Water inlet Water outlet Air outlet, do not obstruct Control box
Power cable connection
61AF 045-055 units with and without hydronic module
1000 1000 1000 1000
Notes: A Non-certified drawings. Refer to the certified dimensional drawings supplied with the unit or available on request, when designing an installation. For the location of fixing points, weight distribution and coordinates of the centre of gravity refer to the certified dimensional drawings. B In multiple-unit installations (maximum four units), the side clearance between the units should be increased from 1000 to 2000 mm. C The height of the solid surface must not exceed 2 m.