SINGLE-EFFECT STEAM-FIRED ABSORPTION CHILLERS 16TJ 11-53
5 7 6
Legend 1. Condenser 2. Steam inlet 3. Generator 4. Chilled-water outlet 5. Control panel 6. Evaporator 7. Chilled-water inlet 8. Cooling water inlet 9. Heat exchanger 10. Heat reclaimer 11. Absorber
Scope of supply
1. Standards met The units comply with the following standards: - ARI 560-2000 - 2006/42/EC (machine directive) - 2006/95/EC (low-voltage directive) - 2004/108/EC (electromagnetic compatibility directive) - 97/23/EC (pressure equipment directive). 2. Absorption chiller, comprising: 1. Lower shell - Evaporator and refrigerant dispersion tray - Absorber and absorbent dispersion tray with eliminators - Bases. 2. Upper shell - Generator with eliminators - Condenser with eliminators - Rupture disk. 3. Heat exchangers with refrigerant drain heat reclaimer 4. Pumps - Absorbent pump with isolating valves - Refrigerant pump with isolating valves - Purge pump. 5. Purge unit - Purge tank with ejector device - Diaphram valves and piping with liquid trap - Pressure sensor - Palladium cell with heater. 6. Control panel - Controller with data display - LEDs and operation buttons - Inverter for absorbent pump (option) - Circuit breaker - Transformer - Relays and terminal blocks - Purge pump operation switch. 7. Locally mounted parts - Temperature sensors - Chilled-water ﬂow switch. 8. Interconnecting piping and wiring - Refrigerant and absorbent piping - Internal power and control wiring. 9. Initial charge - Absorbent (lithium bromide) - Refrigerant (water) - Inhibitor (lithium molybdate).