30RBSY 090-120 units with and without hydronic module
Legend: All dimensions are given in mm
Control box Water inlet Water outlet
Required clearances for air entry Recommended space for maintenance Air outlet, do not obstruct Power supply inlet
* Overall dimensions
Notes: A Non-certiﬁed drawings. Refer to the certiﬁed dimensional drawings supplied with the unit or available on request, when designing an installation. For the location of ﬁxing points, weight distribution and coordinates of the centre of gravity refer to the certiﬁed dimensional drawings. B Provide a gutter around the unit to collect the condensate water or install the accessory condensate collection pan. C The unit must be installed level (less than 2 mm per metre deviation in both axes). D Units are equipped with a sleeve on the air heat exchanger side to allow connection of a suction air frame.