AIR-COOLED LIQUID CHILLERS 30RBS 039-160
Touch Pilot Junior control
The Touch Pilot Junior features a control with advanced communication technology over Ethernet (IP), user-friendly and intuitive user interface with 4.3” colour touch screen. Energy management - Monitoring of the cooling and pumping energy use on Touch Pilot user interface with optional electricity meter Integrated advanced communication features - Easy and high-speed communication technology over Ethernet (IP) to a building management system - Access to multiple unit parameters. 4.3’’ Touch Pilot Junior user interface Intuitive and user-friendly 4.3 inch touch screen interface Concise and clear information is available in local languages Complete menu, customised for different users (end user, service personnel or Carrier engineers).
Evaporator Entering water temperature at start-up Leaving water temperature during operation Entering/leaving water temperature difference Condenser Entering air temperature, full load*** Entering air temperature, part load*** Hydronic module**** Entering air temperature Kit without pump Kit with pump (option 116x) Kit with pump (option 116x) and frost protection option to -20°C (option 42) °C °C K
7.5* 5** 3
Outside air temperature, °C
45 35 25 15
30 20 10
-5 -15 -25 0 5 10 15
°C °C °C
-20 -10 -20
Note: This operating range applies up top 130 Pa static pressure without suction air duct for sizes 070 and 080 and 140-160, and up to 240 Pa for all other sizes.
Note: Do not exceed the maximum operating temperature. * ** For entering water temperatures below 7.5°C at start-up, contact Carrier. For low-temperature applications, where the leaving water temperature is below 5°C, a frost protection solution must be used. *** Ambient temperature: Please refer to option 20 for low-temperature applications (< -10°C). For transport and storage of the 30RBS units the minimum and maximum allowable temperatures are -20°C and +48°C. It is recommended that these temperatures are used for transport by container. **** Deﬁnes the frost-free temperature of the hydronic components for use without glycol.